Runtime chart for OMNIVSINT1000
Runtime tests are performed with new, fully charged batteries under typical office or data center environmental conditions.
The runtimes presented here are estimates based on actual data points.
The Cisco compatible logo signifies that Tripp Lite's product has undergone interoperability testing by Tripp Lite together with Cisco and a third-party test house based on testing criteria set by Cisco. Tripp Lite is solely responsible for the support and warranty of its product. Cisco makes no warranties, express or implied, with respect to Tripp Lite's product or its interoperation with the listed Cisco product(s) and disclaims any implied warranties of merchantability, fitness for a particular use, or against infringement.
Cisco, the Cisco logo, and Cisco Systems are trademarks or registered trademarks of Cisco Systems, Inc. and/or its affiliates in the United States and certain other countries.
Email a Page Link
Tripp Lite's OMNIVSINT1000 line interactive UPS system offers voltage regulation, surge suppression and long lasting battery support for personal computers, internetworking equipment and other sensitive electronics. Internal UPS circuits support entry level PC systems for up to 60 minutes during power failures so that connected equipment can be shut down without data loss. Automatic Voltage Regulation (AVR) circuits regulate brownouts as low as 159 volts back to usable levels without using battery power. Offers complete desktop power protection in an attractive black tower configuration. Includes 6 outlets with battery support and AC surge suppression. USB port enables optional unattended system shutdown without data loss in the case of extended power failure, USB cable included. PowerAlert software available via free download from www.tripplite.com. Built-in single line RJ phone surge suppression jacks protect modem, fax machine, cordless phone or other peripheral with a standard dialup/DSL phone connection. Built-in audible alarm and 4 front panel LEDs indicate line power status, battery power status, battery low/replace status and load status. 1000VA power handling ability supports entry-level PCs, network workstations, point-of-sale equipment, small business phone systems, audio/video equipment and home theater systems. Offers 5 minutes battery runtime with a full load of 1000VA and 12 minutes with a half load of 500VA. Supports battery replacement via built-in access panel.
- OMNIVSINT1000 Uninterruptible Power Supply offers voltage regulation, surge suppression and long lasting battery support
- Supports entry level PCs up to 60 minutes during blackouts to enable shutdown without data loss
- Regulates brownouts as low as 159 volts back to usable levels without using battery power
- 6 IEC320 C13 outlets with complete AC surge suppression
- C14 accepts user-supplied AC power cord with country-specific plug
- USB port and cable enables unattended shutdown in the case of extended power failure
- PowerAlert software available via free download from www.tripplite.com
- Single line phone surge suppression protects standard dialup/DSL phone connection
- Audible alarm and 4 front panel LEDs offer complete UPS and line power status information
- 1000VA power handling ability supports a variety of sensitive electronic equipment
- 5 minutes full load runtime (1000VA), 12 minutes half load runtime (500VA)
- Supports battery replacement via built-in access panel
- Optional PDUBHV10 bypass PDU enables hot-swappable UPS replacement with no disruption to connected equipment
- Attractive full color retail packaging
- OMNIVSINT1000 line interactive UPS
- 2 C13 to C14 interconnection cables
- USB and phone line cables
- Owner's manual with warranty information
|Output Volt Amp Capacity (VA)||1000|
|Output Watt Capacity (Watts)||500|
|Nominal Output Voltage(s) Supported||220V; 230V; 240V|
|Nominal Voltage Details||230V inverter nominal voltage output|
|Frequency Compatibility||50 / 60 Hz|
|Output Voltage Regulation (Battery Mode)||+/- 5%|
|Output Receptacles||(6) C13|
|Included Output Power Cables||Includes 2 C13 to C14 output power cables|
|Hot-Swap PDU options||PDUBHV10 (2U / 8 C13 outlets)|
|Output AC Waveform (AC Mode)||Sine wave|
|Output AC Waveform (Battery Mode)||PWM sine wave|
|Rated input current (Maximum Load)||2.4A|
|Nominal Input Voltage(s) Supported||230V AC|
|UPS Input Connection Type||C14 inlet|
|UPS Input Connection Description||Attached 15cm line cord with C14 inlet. The C14 inlet accepts a user-supplied AC power cord with country specific plug.|
|UPS Input Cord Length (ft.)||0.5|
|UPS Input Cord Length (m)||0.2|
|Full Load Runtime (min.)||5 min. (500w)|
|Half Load Runtime (min.)||12 min. (250w)|
|DC System Voltage (VDC)||12|
|Battery Recharge Rate (Included Batteries)||Less than 9 hours from 10% to 90%|
|Internal UPS Replacement Battery Cartridge||RBC51|
|Battery Access||Battery access door|
|Battery Replacement Description||Hot-swappable, user replaceable batteries|
|Voltage Regulation Description||Automatic voltage regulation (AVR) maintains line power operation with input voltage as low as 159|
|Undervoltage Correction||Input voltages between 159 and 199 are boosted by 14%|
LEDS ALARMS & SWITCHES
|LED Indicators||4 LEDs indicate line power, battery power, overload and battery low/replace status|
|Audible Alarm||Audible alarm indicates power-failure and low-battery conditions|
|Alarm Cancel Operation||Power-fail alarm can be silenced using alarm-cancel switch; once silenced, alarm will re-sound to indicate low-battery status|
|Switches||2 Switches control off/on power status and alarm-cancel/self-test operation|
SURGE / NOISE SUPPRESSION
|UPS AC Suppression Joule Rating||508|
|UPS AC Suppression Response Time||Instantaneous|
|UPS Dataline Suppression||1 line TEL/DSL (1 in / 1 out)|
|EMI / RFI AC Noise Suppression||Yes|
|Installation Form Factors Supported with Included Accessories||Tower|
|Installation Form Factors Supported with Optional Accessories||Wallmount (UPSWM - tower mounting kit)|
|Primary Form Factor||Tower|
|UPS Power Module Dimensions (hwd, in.)||10.8 x 5.2 x 7.5|
|UPS Power Module Dimensions (hwd, cm)||27.3 x 13.3 x 19|
|UPS Power Module Weight (lbs.)||16.7|
|UPS Power Module Weight (kg)||7.6|
|UPS Shipping Dimensions (hwd / in.)||14 x 8.5 x 11|
|UPS Shipping Dimensions (hwd / cm)||35.6 x 21.6 x 27.9|
|Shipping Weight (lbs.)||19.7|
|Shipping Weight (kg)||8.9|
|UPS Housing Material||PVC|
|Operating Temperature Range||+32 to +104 degrees Fahrenheit / 0 to +40 degrees Celsius|
|Storage Temperature Range||+5 to +122 degrees Fahrenheit / -15 to +50 degrees Celsius|
|Relative Humidity||0 to 95%, non-condensing|
|AC Mode BTU / Hr. (Full Load)||147.8|
|Battery Mode BTU / Hr. (Full Load)||254|
|AC Mode Efficiency Rating (100% Load)||92%|
|PowerAlert Software||Free download from www.tripplite.com|
|Communications Cable||USB interface cable included|
|WatchDog Compatibility||Supports Watchdog application, OS and hard-reboot restart options for remote applications|
LINE / BATTERY TRANSFER
|Transfer Time||4 milliseconds|
|Low Voltage Transfer to Battery Power (Setpoint)||159|
|High Voltage Transfer to Battery Power (Setpoint)||Yes|
|Cold Start (Startup in Battery Mode During a Power Failure)||Cold-start operation supported|
|High Availability UPS Features||Hot swappable batteries|
|UPS Certifications||CE; Tested to GOST (Russia); Tested to SASO (Saudi Arabia); Tested to IRAM (Argentina); Meets FCC Part 15 Category B (EMI)|
|UPS Certification Details||CE IEC62040|
|Product Warranty Period (International)||2-year limited warranty|
|Product Warranty Period (Mexico)||2-year limited warranty|
|Product Warranty Period (Puerto Rico)||2-year limited warranty|
† Tripp Lite uses primary and third-party agencies to test its products for compliance with standards. See a list of Tripp Lite's testing agencies.
Ask your questions. Share your answers.
My Omnivsint1000 UPS stopped charging the battery.
At first i thought the battery was getting old so i replaced them with new batteries but then the new ones also didn't get charged and when the power is out the UPS turns off almost instantly.
I have a battery charger so i thought of charging the batteries with it then install them in the UPS while they are charged as a temporary solution till i find out why the UPS does not charge the batteries but then i noticed the the UPS is doing a strange thing; it some times reset all by itself shutting down and then opening again; turning off all connected hardware in the process! even though it is plugged in and the batteries are fully charged with my battery charger.
What could possibly be the reason for all of this and how to solve that?
Thanks for your help in advance, i'm really in deep need for the UPS to finish some renders for work and i totally rely on it save the work when electricity goes off.
How long have you had the unit?
Also, since you started using the UPS system has any equipment been added to the application?
Do you have the specific makes and models of products planning to be connected to the UPS system? May I please have those makes/models?
I'm wondering if the unit might be past the typical lifespan of if the unit is undersized.
How long have you had the UPS system?
In order to best assist can you provide a more info in regards to what's being connected to the UPS?
Also before the unit decided not to power on, was it currently plugged in? Did anything happen while it was plugged in? (surge, spike, storm)
The UPS system will not support 208 vac.
Please know we have various other UPS systems in our offering that will support 208 vac.
For assistance with an alternate UPS system, please reach out to our presales help line at 773-869-1773 or via email at firstname.lastname@example.org.
UPS Systems: UPS Battery Packs & Accessories
Power Management: Software
Extended Warranties & Start-Up/On-Site Services: Extended Warranties
This product has a 2-year limited warranty. Get more information
Software & Downloads
- Runtime Chart for UPS Model OMNIVSINT1000[pdf - 15 Kb]
- Owner's Manual for OMNIVSINT800/OMNIVSINT1000/OMNIVSINT1500XL UPS 932205[pdf - 919 Kb]
- Sealed Lead-Acid Battery Material Safety Data Sheet (MSDS) (English)[pdf - 128 Kb]
- PowerAlert Power Management Software[free download]
Free Power Management Software for your OMNIVSINT1000
Runtime at Full Load
5 min. (500w)
Runtime at Half Load
12 min. (250w)
Do you own a OMNIVSINT1000?
Get all your support resources in one place.go to model support→
Tripp Lite has a policy of continuous improvement. Specifications are subject to change without notice.
How can we improve the information on this page? Is an important specification missing? Did you spot an error? Please let us know how we can make this information more useful to you.